Gree Compatibility: Inverter ducted, single phase units only, R401A gas type only
GUD###PHS/B-S /// GUD###W/Nh B-S
Gree are using the same model numbers for their new R32 Gas type units, we are not compatible with these units at this stage
Can use RA as controlling sensor
Cannot use Zones, Master or RF as controlling sensor
Polarity is critical see below, for correct connection
Requires Gree proprietary controller for setup
Connect the Gree proprietary wired controller to the FCU PCB
Enter the service mode parameters
To enter Service Mode, power must be connected to the unit and proprietary wired controller, and the unit must be switched 'OFF' at the wall control. Follow the steps below and refer to the function and parameter setting table
As per the instructions set the sensor to return air for all modes
Set the iZone control setting
Set the required static pressure setting
Cycle the power to the AC unit
Connect a 2 core, twisted pair control cable from the C225 / C325G X / Y to CN1 in the fan coil unit
A connector and short cable has been provided with the C325G but will need to be extended
Service Mode Parameter Table
Temp sensor location
Ensure set to '01'
Sensor at return air for all modes
Sensor at wired control for all modes
Sensor at return air for cool, dry & fan modes, at wired control for heat mode
Ensure set to '01'
iZone control setting
Indoor fan power setting
Factory default '05'
Adjust to suit installed static
Low static = '01'
High static = '09'
Indoor fan coil unit PCB: Note connector CN1
Connector and short cable provided: Insert the connector and short cable (see image below) into the connector CN1. Note the correct polarity for X & Y. Polarity is critical
C225 AC unit connector: Connect AC unit cable from fan coil to C225 as indicated
Polarity is critical: Make sure it is wired in accordance with these instructions on both the CN1 connector on the fan coil PCB and the C225 cable connector
Cable from CN1: Connect a shielded, 2 core, twisted pair cable to the connector and short cable provided